Applies to electronic direct a.c. converter systems with electrical energy storage means in the d.c. link. Ensures continuity of an alternating power source. Also includes the method of specifying all power switches that form integral parts of a UPS and are associated with its output. Included are interrupters, bypass switches, isolating switches, load transfer switches and tie switches. does not refer to cnventional mains distirbution boards, rectifier input switches or d.c. switches or UPS based on rotating machines. Defines a complete uninterruptible power system in terms of its performance and not individual UPS functional units. The contents of the corrigendum of July 2003 have been included in this copy.
|Included in IECEE System|
|Test Report Form|
|Testing Equipment List|
No information declared
DISCLAIMER: National differences
The National differences and Group differences, National Deviations and Special National conditions (SNC), are based solely on information provided to the Secretariat by the IECEE Member Bodies and/or NCBs and other sources. The IEC/IECEE is not responsible for, nor will it take any position related to, the accuracy or validity of the information provided. To verify the current status of this type of information, we recommend contacting the Member Body (MB) or National Certification Body (NCB) of the relevant country.
Group Differences are applicable for CENELEC member countries: Austria, Belgium, Bulgaria, Croatia, Cyprus, the Czech Republic, Denmark, Estonia, Finland, France, Germany, Greece, Hungary, Iceland, Ireland, Italy, Latvia, Lithuania, Luxembourg, Malta, the Netherlands, Norway, Poland, Portugal, Republic of North Macedonia, Romania, Serbia, Slovakia, Slovenia, Spain, Sweden, Switzerland, Turkey and the United Kingdom.
Responsible National Certification Body
Taoyuan City 333
United States of America